773 Words4 Pages

CHAPTER 3

POWER QUALITY AND ITS PROBLEMS

3.1 Harmonics

Power systems are designed to operate at frequencies of 50 or 60 Hz. However, certain types of loads produces currents and voltages with frequencies that are integer multiples of the 50 or 60 Hz fundamental frequency. These frequencies components are a form of electrical pollution known as harmonic distortion. There are two types of harmonics that can be encountered in a power system. Synchronous harmonics. Asynchronous harmonics.

Synchronous harmonics are sinusoids with frequencies which are multiples of the fundamental frequency. The multiplication factor is often referred to as the harmonic number. The synchronous harmonics can be subdivided into two categories. Sub-harmonics:*…show more content…*

Transformer exciting current, arc furnaces, rectifiers and many other loads will produce harmonics in the utility lines. Most utilities limit the allowable harmonic current levels to the values shown in IEEE 519.

3.1.1 Total Harmonic Distortion (THD)

The total harmonic distortion of a signal is a measurement of the harmonic distortion present in current or voltage. It is defined as the ratio of the sum of the powers of all harmonic components to the power of the fundamental frequency. Harmonic distortion is caused by the introduction of waveforms at frequencies in multiplies of the fundamental.

THD(%)=√(∑_(i=2)^α▒x_i^2 )/|x_1 | (2.2)

The THD is a very useful quantity for many applications. It is the most commonly used harmonic index. However, it has the limitation that, it is not a good indicator of voltage stress within a capacitor because that is related to the peak value of voltage waveform.

3.1.2 Distortion Factor

The distortion factor Fd is defined as the ratio between the fundamental and the signal in RMS values. It is given*…show more content…*

They may be trapped by power factor correction capacitors and overload them or cause resonant over-voltages. They can distort the feeder voltage enough to cause problems in computers, telephone lines, motors, and power supplies, and may even cause transformer failures from eddy current losses. The harmonic currents may be trapped by installing series LC filters resonant at the offending frequencies. These filters should be designed to offer low impedance at the resonant frequency compared to the source impedance at that frequency. But, again, there is a hidden “gotcha.” If a filter is installed that has a series resonance at the 7th harmonic, it will also have a parallel resonance with the utility at a lower frequency when the source inductance is added to the filter inductance. If this parallel resonance should lie on or near the 5th harmonic, there is the possibility of the resonant over-currents described earlier. The installation of series resonant traps will always introduce parallel resonances at frequencies below the trap frequencies. Good practice dictates that multiple resonant traps be installed first at the lowest harmonic frequency

POWER QUALITY AND ITS PROBLEMS

3.1 Harmonics

Power systems are designed to operate at frequencies of 50 or 60 Hz. However, certain types of loads produces currents and voltages with frequencies that are integer multiples of the 50 or 60 Hz fundamental frequency. These frequencies components are a form of electrical pollution known as harmonic distortion. There are two types of harmonics that can be encountered in a power system. Synchronous harmonics. Asynchronous harmonics.

Synchronous harmonics are sinusoids with frequencies which are multiples of the fundamental frequency. The multiplication factor is often referred to as the harmonic number. The synchronous harmonics can be subdivided into two categories. Sub-harmonics:

Transformer exciting current, arc furnaces, rectifiers and many other loads will produce harmonics in the utility lines. Most utilities limit the allowable harmonic current levels to the values shown in IEEE 519.

3.1.1 Total Harmonic Distortion (THD)

The total harmonic distortion of a signal is a measurement of the harmonic distortion present in current or voltage. It is defined as the ratio of the sum of the powers of all harmonic components to the power of the fundamental frequency. Harmonic distortion is caused by the introduction of waveforms at frequencies in multiplies of the fundamental.

THD(%)=√(∑_(i=2)^α▒x_i^2 )/|x_1 | (2.2)

The THD is a very useful quantity for many applications. It is the most commonly used harmonic index. However, it has the limitation that, it is not a good indicator of voltage stress within a capacitor because that is related to the peak value of voltage waveform.

3.1.2 Distortion Factor

The distortion factor Fd is defined as the ratio between the fundamental and the signal in RMS values. It is given

They may be trapped by power factor correction capacitors and overload them or cause resonant over-voltages. They can distort the feeder voltage enough to cause problems in computers, telephone lines, motors, and power supplies, and may even cause transformer failures from eddy current losses. The harmonic currents may be trapped by installing series LC filters resonant at the offending frequencies. These filters should be designed to offer low impedance at the resonant frequency compared to the source impedance at that frequency. But, again, there is a hidden “gotcha.” If a filter is installed that has a series resonance at the 7th harmonic, it will also have a parallel resonance with the utility at a lower frequency when the source inductance is added to the filter inductance. If this parallel resonance should lie on or near the 5th harmonic, there is the possibility of the resonant over-currents described earlier. The installation of series resonant traps will always introduce parallel resonances at frequencies below the trap frequencies. Good practice dictates that multiple resonant traps be installed first at the lowest harmonic frequency

Related

## Vibrating Beam Lab Report

1571 Words | 7 PagesThe equivalent standard form is: (x_1 ) ̈+[2ξω_n ] (x_1 ) ̇+[ω_n^2 ] x_1=0 This is the standard equation of motion of a single degree-of-freedom vibrating system in which 휔푛 and 휉 are known as the natural frequency and damping ratio respectively. These are important parameters in a mechanical system as they characterise the dynamic response. By inspection of [7] and [8], the theoretical natural frequency, 휔푛 (푟푎푑 푠 −1 ), is given by ω_n=√((kl_4^2)/(I_beam+Ml_1^2+m_motor l_2^2 )) For the calculation of the damping factor 휉, the ratio of 푛 successive oscillation amplitudes (푋0,1, …푋푛) is ln x_0/x_n =nδ=2πξn where 훿 is the logarithmic decrement. The logarithmic decrement (훿) can be measured experimentally and used to calculate 휉, which is easier than measuring 퐶. The standard solution to equation [8] when 휉 < 1 (underdamped) is given by x_1 (t)=Ae^(-ξω_n t) cos(tω_n √(1-ξ^2 )+∅_1 where 퐴 and 휙1 are determined from the initial conditions of displacement and velocity.

## Oscilloscope Lab Report

2305 Words | 10 PagesThe measurement from two devices were observed and recorded in Table 1 and Table 2 . The DC power supply was replace with an AC power supply which has frequency of 5kHz as shown in Figure 4 below. Figure 4: Schematic diagram of a series circuit connecting to AC power supply and two resistor. The voltage across and current flow each resistor was measured by using DMM and then by using oscilloscope. The measurement including from two devices were observed and recorded in Table 3 and Table 4 .

## Crystal Chemistry Lab Report

996 Words | 4 PagesBond length O-P-O angle also causes tetrahedral distortion at elevated temperature although not as significant as compared to tetrahedral tilt. Therefore, we can conclude that tetrahedral distortion is caused by tetrahedral tilt and also very sensitive to temperature. Temperature dependence of this angle δ can be expressed by the

## Steam Engine As A Forced Oscillator Essay

1408 Words | 6 PagesSo if there is no resistance this system could act like simple harmonic motion, but there is resistance in the system which means without the force it is a damped system and because of this force it has to be classified as a forced oscillator. So all of the forces have to act in perfect harmony to keep the oscillating motion going or else this oscillator will no act like a forced oscillator and will act like a damped oscillator or a simple harmonic

## Fepo4 Aquatic Analysis

1244 Words | 5 PagesThis would also further culminate in high amplitude kind of vibration in the alpha quartz. This particular outcome from this condition would result in a quartered total neutron scattering structure. The tetrahedrons’ distortion is defined as the time when the angles and bond lengths are varying altered. On the other hand, this differs with tetrahedron tilting, since tilting is the time where only the bond angles are different. The Fe-O-P angles would also enlarge and tilt when the temperature has risen above 500 degrees Celsius.

## Essay On Simple Harmonic Motion

759 Words | 4 PagesSimple Harmonic Motion The world contains many laws of motion which help govern the world as we know it. Although most people are blind to these important laws, they impact almost every aspect of our lives. One of the most evident types of motion is periodic motion, or more specifically, simple harmonic motion. According to Britannica, simple harmonic motion is a “repetitive movement back and forth through an equilibrium, or central, position, so that the maximum displacement on one side of this position is equal to the maximum displacement on the other side” (The). Some examples of this interesting type of motion include a swing on the play set, the vibrating strings of a guitar, and the springs on a vehicle.

## Clogged Bed Literature Review

1073 Words | 5 PagesThe research concluded that the main filtration mechanism in deep filter bed is the attachment of particles onto the surface grains [7]. Straining and arching were not the main particle removal mechanism [7]. Among the list of clogged bed equation, it was noticed that the two equations that does not requires empirical constant was Ornatskii’s equation and Mint’s equation, as shown by equation (1.2.4a) and equation (1.2.4b). 〖HL〗_3/〖HL〗_0 =〖[1+〖(β_3 σ/ε_0)〗^(1⁄2)]〗^3/〖[1-β_3

## Power Quality Research Paper

852 Words | 4 Pages• Transient voltages and currents. • Harmonic content in the waveform for ac power. • Continuity of service. The electric utilities and the consumers are becoming more and more concerned about the end use of electrical power. Sensitive loads such as computers, PLC, variable speed drives etc.

## Causes Of Deafness

884 Words | 4 PagesThe ear may be damaged by being exposed to very loud sounds (high volume on the mp3 player or work) that can damage the tympanic membrane, or fluid in the middle ear from colds. In addition deafness is also caused by sound vibrations not being transmitted effectively in the ear. And as it is

## Advantage And Disadvantages Of Automation

2541 Words | 11 PagesThe size of the inductive coil and the capacitor are matched to produce a self-sustaining sine wave oscillation at a fixed frequency. The coil and the capacitor act like two electrical springs with a weight hung between them, constantly pushing electrons back and forth between each other. Electrical energy is fed into the circuit to initiate and sustain the oscillation. Without sustaining energy, the oscillation would collapse due to the small power losses from the electrical resistance of the thin copper wire in the coil and other parasitic

### Vibrating Beam Lab Report

1571 Words | 7 Pages### Oscilloscope Lab Report

2305 Words | 10 Pages### Crystal Chemistry Lab Report

996 Words | 4 Pages### Steam Engine As A Forced Oscillator Essay

1408 Words | 6 Pages### Fepo4 Aquatic Analysis

1244 Words | 5 Pages### Essay On Simple Harmonic Motion

759 Words | 4 Pages### Clogged Bed Literature Review

1073 Words | 5 Pages### Power Quality Research Paper

852 Words | 4 Pages### Causes Of Deafness

884 Words | 4 Pages### Advantage And Disadvantages Of Automation

2541 Words | 11 Pages